Odd power PDU problem

Do you have a question? Post it now! No Registration Necessary.  Now with pictures!

•  Subject
• Author
• Posted on
QN: do I have a bad PDU?

Symptoms:
3  servers, each connecting to 2 PDU's via dual power supplies.
Each PDU was showing 6.3 A load. (15 A max.)

When moving all 3 outlets off PDU so it could be physically moved, PDU

The nameplate load of the 3 servers is > 15A, but the combination of 2
x 6.3 (measured Amps) is not.

So, it seems either:
- the measurements of 6.3 A on each circuit is incorrect
- there is a power draw spike when servers switch from 2 power supplies
to 1.

Does anyone know if the latter case is true?
Or have other theories?
Thanks

Re: Odd power PDU problem

stevergfrancis@gmail.com wrote:

There are some pictures here, of what the current consumption of
a computer power supply looks like. They show an oscilloscope
trace for PFC (power factor corrected) and non-PFC supplies. I know
my clamp-on ammeter has a lot of trouble giving a correct readout
on my non-PFC ATX supplies, for a computer in sleep, and it could
be the ammeter on the PDU is not measuring what you think it is.

http://www.xbitlabs.com/articles/other/display/psu-methodology_8.html

Power factor is why there is a difference between the "watts" and
"VA" rating of equipment. The first article that came up in a

http://ecom.mysylvania.com/miniapps/lightingcenter/PDFs/faq0002-0297.pdf

It could be the PDU display shows "watts", and the breaker is
seeing (2x6.3)/0.7 = 17.8A ?

Paul

Re: Odd power PDU problem

Paul wrote:

... snip ...

There is no such thing as power factor for DC, which is what the
output of a power supply is.  You can talk about it on the input
(mains) circuit.  Power factors involve the phasing, which in turn
requires AC.  Thus, on the DC side, watts = V * A.

--
"If you want to post a followup via groups.google.com, don't use
the broken "Reply" link at the bottom of the article.  Click on
"show options" at the top of the article, then click on the